Update: Firmware 1.41 has been replaced with 1.43 that has more bug fixes and enhancements. Info can be found here:
This page features information regarding the beta firmware for the LZW31-SN that was released on 03/27/2020. This firmware is intended for users that would like to test the fixes and features included in this release before it goes into production. It should be a fairly stable release that fixes several issues.
The attached .otz file is the Z-Wave Chip Upgrade that is target 0 in the Z-Wave PC Controller software.
The Holtek .bin file is the LED bar MCU firmware and is target 1 in the Z-Wave PC Controller software.
Updating the firmware is a fairly safe & fool proof procedure with Z-Wave. Please double check you are updating the correct device with the appropriate model number. Do not interrupt power to the device while the update is taking place.
Fixed Energy & power reporting not being disabled when configuration options are set to 0.
Fixed Power reports flooding network when bulb power consumption fluctuates frequently.
Homeseer: Fixed not processing BasicReports when sent after turning switch on/off from the wall. Changed to SwitchMultiLevelReport.
Vera: Fixed association purging issue. Vera was not properly processing group #4 group name. Shortened the name to resolve this issue.
Fixed state sometimes not being restored properly when local protection is enabled.
Fixed dimmer turning off when level rises above 80% on certain circuits. Make sure parameter 21 & 22 are set correctly.
Fixed an issue where when the user sets parameter 5 in switch config mode it causes an exception.
Fixed additional bugs for setting configuration parameters in switch config mode for parameters 5,9,10,11.
Fixed an issue where holding the down key to adjust a device in association group 4 would sometimes turn it off.
Fixed a bug where the duration of parameter 17 is far from the expected value.
Fixed an issue where the interval time of Central Scene notification is far from the expected value.
Fixed the issue of sending two Meter reports when the device is powered on.
Notifications no longer turning off when user adjusts the level or performs various other actions on the switch.
Changing minimum level to 10% to accommodate likely use of LED bulbs.
Change the range of parameter 19 to 0,30-32767 to prevent users from choosing a value that may flood the network.